NEC Amps, Amperes from NEC Tables 430.247, 430.248, and 430.250.
This table calculates the appropriate standard fuse and breaker sizes, shown in amperes,
from the values listed in NEC 240.6(A). The table is derived from NEC Table 430.52.
Minimum motor circuit conductor = NEC Amperes X 125%"
|Type of Motor||Nontime Delay Fuse||Dual Element (TD) Fuse||Instantaneous Trip Breaker||Inverse Time Breaker|
Note: NEC 240.4(C)
Where the overcurrent device is rated over 800 amperes, the ampacity of the conductors it protects shall be equal to or greater than the rating of the overcurrent device defined in 240.6.