Rising Edge Services, LLC
Minimum Conductor Ampacity and Size Calculator
This calculator is based on NEC Table 310.15(B)(16).
Refer to NEC Articles 110.14(C), 210.19(A)(1), 430.22, Ch. 9 Table 8, etc. for more information.
Inputs for calculating Minimum Conductor Ampacity and Size,
Continuous Load, in Amperes, "CL"
Non-Continuous Load, in Amperes, "NCL"
Number of Current Carrying Conductors in the Raceway,
Optional Inputs: Used for Voltage Drop and Wire Size Correction for Long Cable Runs
Circuit Length in Feet, ONE WAY, "D"
Max Percent VD,
Max % VD
Select Three Phase or Single Phase,